Installation manual. 1. The kit includes the following parts: 1. Remove the upper part of remote controller (Refer to figure 1). Insert a minus screwdriver into the. this operation manual before using the air conditioner. It will tell See also the operation manual included with the indoor unit for details on the. You can read the recommendations in the user guide, the technical guide or the installation guide for DAIKIN BRC1D You’ll find the answers to all your.
|Published (Last):||20 September 2004|
|PDF File Size:||4.30 Mb|
|ePub File Size:||13.46 Mb|
|Price:||Free* [*Free Regsitration Required]|
Be careful not distort the shape of the lower part of remote brcc1d52 by overtightening mounting screws. It’s a community-based project which helps to repair anything. Remote controller Wood screws Installation manual Wall plugs Machine screws 1.
Manual BRC1D52 Daikin
Refer to figure 5. The switch box and wiring for connection are not included. Permission level function 6.
Set the remote controller before turning the power supply on. Refer to the instruction manual for each optional accessory. Not displayed if the indoor unit is not equipped with that function. Remove the upper part of remote controller Refer to figure 1 Insert a minus screwdriver into the slots 1 in the lower part of the remote controller 2 placesand remove the upper part of the remote controller.
Do not directly touch the PC board with your hand. Long life filter Approx. Refer to the chapter “Field settings”.
Daikin Manual BRC1D52 Termostato
First begin fitting from the clips at the bottom. Change setting when ultra-long filter is installed 2 Thermostat sensor in remote controller 3 Spacing time of display time to clean br1cd52 filter count setting for when the filter sign is not to be displayed 0 15 25 Approx. Be careful not to damage the board with the minus screwdriver. Refer to figure 8.
The kit includes the following parts: NOTE When wiring, run manuall wiring away from the power supply wiring in order to avoid receiving electric noise external noise. Reattach the upper part of the remote controller Be careful not to pinch the wiring when attaching.
Setting is carried out in the group mode, however, if the mode number inside the parentheses is selected, indoor units can also be set individually. During this time the remote controller can not be operated.
Refer to figure 4: The PC board is mounted in the upper part of the remote controller. Do not make any settings not given in the table. Wire the indoor unit 1 Refer to figure 6 NOTE indoor unit 2 lower part of the remote controller 3 upper part of the remote controller 4 wired from the rear 5 wired from the top 6 notch the part for the wiring to pass through with nippers, etc. This operation is unnecessary when setting by group. P1 and P2 do not have polarity. If required, you can limit the user action by restricting the number of operable buttons.
Connect the terminals on top of the upper part of the remote controller P1, P2and the mxnual of the indoor unit P1, P2.